Carley Round
ID : 4754
LED 2700K, 4000K, 5700K 230-240Vac CRI >80 MacAdam step 3
Input power : 40W
Height  3500mm
Light Distribution  360°
Electronic driver ON/OFF
CE and BIS

LUMINAIRE TYPE
Light Column. IP rating IP65
MATERIAL CHARACTERISTICS
Extruded aluminium bottom pipe (grade 6063 with test certificate) Ø166 x 3mm thickness, extruded aluminium stem with inner ribbed 45 x 21 x 2mm thickness, extruded aluminium top pipe with inner ribbed. SS fasteners. Pre treated silicone gaskets. PDC aluminium service door 448mm height x 110mm width at 325mm height above the base plate shall be provided with the company logo embossed on the bottom of the door and safety rope. The control gear tray is prewired with 2.5 Sq.mm cable, 6A MCB and 32A terminal connectors for loop-in / loop-out arrangement.
MS mounting plate Sq. 250 x 12mm thick steel of grade E250 to IS 2062:2011 with 4 elongated holes 38 x 19 to suit M16 bolts at CC180. This mounting steel plate along with foundation bolts of suitable size to be used for ensuring firm grouting into the specially designed foundation pole. Hot dip galvanised foundation bolt. Mechanical resistance IK08.
Pure polyester powder coated process : Mild shot blast &  pure polyester powder coating.
LIGHTING PERFORMANCE
Optical grade clear toughened glass diffuser of 4mm thickness with controlled downward light emission. Lamp fixed position.
CARLEY ROUND
This luminaire contains built-in LED modules. LED modules are engineered accordingly to the existing regulations of Lumen Maintenance (LM80) and Technical Memorandum (TM21), Lifespan of the luminaire > 60,000 hours at 40°C. Operating ambient temperature range is from -15°C to +50°C. Driver efficiency >87%, power factor >0.95, THD <10%, Surge protection 5KV. 